Figure 4-5. Housing covers.
Inspection and Repair. C l e a n ,
inspect and repair covers as follows:
( 1 ) Brush off any loose dirt or foreign matter
from gaskets and insulation. Wipe off tops of metal
parts with a cloth dipped in cleaning solvent (Fed.
Spec. P-D-680). Wash dirt from condenser cover.
( 2 ) I n s p e c t m e t a l c o v e r s f o r d i s t o r t i o n a nd
damaged or loose gaskets and insulation. Inspect
canvas cover for torn condition and for damaged
f a s t e n e r s.
(3) Straighten a bent metal cover, cement or
replace loose or damaged gaskets and insulation
Replace cover if it will not form a satisfactory sea
( 4 ) R e p a i r t o r n
a r e a s of c o n d e n s e r c o v er
Replace cover if damage is extensive.
d. Installation. Refer to figure 4-5 and install
covers as follows:
( 1 ) I n s t a l l t h e r m o s t a t i c s w i t c h b r a c k e t on
center cover and secure with two screws. Install
center cover and six screws.