Install the green wire on the ground plug.
e. Install the new or repaired female receptacle on the wire by
stripping the ends and folding over the contact points.
f. Install. the three captive screws and tighten.
Section IV. TROUBLESHOOTING
This section provides information useful in diagnosing and correct-
ing unsatisfactory operation or failure of the air conditioner and its
components. Each trouble symptom stated is followed by a list of prob-
able causes of the trouble. The possible remedy recommended is de-
scribed opposite the probable cause. Any trouble beyond the scope of
organizational maintenance shall be reported to direct support mainten-
33. Air Conditioner Fails to Start
a. Inspect power cable for
b. Circuit breaker not in
Set circuit breaker.
c. Lower thermostat setting.
c. Conditioned space tempera-
ture below thermostat setting.
34. Cooling Insufficient
a. Replace thermostat (para 42).
a. Thermostat defective.
Clean evaporator assembly
b. Evaporator coil or filter
c. Clean condenser coil (para
c. Condenser coil dirty.
d. Inspect charge through sight
d. Refrigerant charge low.
glass. Report low charge to direct
35. Air Conditioner Stops
a. Inspect power source for
a. Power failure.