Compressor Stops on High Head Pressure
a. Clean condenser assembly
a. Condenser dirty.
37. Cooling Excessive
a. Replace thermostat (para 42).
a. Thermostat defective.
Section V. HOUSING PANELS
The air conditioner is enclosed by aluminum panels, mounted on a
rigid aluminum frame and secured with machine screws and steel fasten-
ers. The air inlet and outlets are provided with louvered panels.
(1) Right-Side Panel.
(a) Disconnect the power source cable assembly from the power
plug (fig. 3).
Loosen screws and remove the right-side panel from the unit.
(2) Front Panel.
(a) Remove the right-side panel as (1) above.
(b) Remove the mounting screws from the panel and tilt the panel
(c) Disconnect the damper linkage.
(d) Remove the knobs from the thermostat and selector switch.
(e) Remove the front instruction plate.
(f) Remove screws from thermostat and selector switch.
(g) Remove front panel.