(b) Inspect motor for damage which would impair serviceability.
(c) Refer to figure 3-5 and inspect for worn bearings.
(3) Test. Check continuity of motor windings for open windings or windings shorted to motor frame. If any of
these conditions are found, replace motor.
(4) Repair. Refer to figure 3-5 and repair fan motor if worn bearings are found during inspection.
(5) Replace. Replace motor if serviceability is impaired by damage, or if test indicates open windings or
windings shorted to motor frame.
(6) Installation. (See figure 3-4.)
Figure 3-5. Fan motor repair