TABLE 4-2. TROUBLESHOOTING (cont.)
TEST OR INSPECTION
Inspect condenser fan for damage
Replace fan. (Refer to paragraph 4-43.)
Make sure that air outlet louvers are not stuck or jammed in closed position.
Free louvers and control cable. Adjust control, or report to direct support maintenance if
actuating cylinder is not working properly.
9. AIR CONDITIONER FAILS TO HEAT.
Check selector switch for improper setting.
Set selector switch to LOW HEAT or HIGH HEAT.
Make sure that temperature control switch is set properly.
Reset switch, if necessary.
Check for dirty evaporator return air filter.
Check evaporator fan motor for proper operation,
Replace bad motor. (Refer to paragraph 4-40.)
Make continuity check of temperature selector switch or mode selector switch.
Replace bad switch. (Refer to paragraphs 4-28 and 4-30.)
Inspect heaters and wiring for loose connections or damage.
Tighten connections and fix bad wiring. Replace bad heater elements. (Refer to paragraph
Replace bad relay. (Refer to paragraph 4-35.)
Check operation of heater high-temperature cutout thermostatic switch. It should open when
temperature rises above setting.
Replace bad thermostatic switch. (Refer to paragraph 4-41.)
10. EXCESSIVE NOISE.
Tighten fans on shafts. Tighten all mounting screws.
excessive side or end play.
Replace worn or bad motor. (Refer to paragraphs 4-40 and 4-43.) (Refer to direct support
maintenance for repairs.)
Listen for compressor knocks or chatter.
Stop air conditioner and report condition to direct support maintenance.