Table 3-1. ORGANIZATIONAL PREVENTIVE MAINTENANCE
CHECKS AND SERVICES (PMCS)
Item To Be
BOTTOM VIEW (FILTER IN PLACE)
Filter, Air Conditioning
Release hook retainer and remove filter.
Clean in a mild detergent and water solution.
Rinse in clear water and shake out excess water.
(See note at end of
Inspect for any damage, such as punctures or cuts that would allow passage
of unfiltered air.
e. Inspect for packed or mashed filter material that would block air flow.
f. Replace filter if found bad.
The return air filter is not a part of the air conditioner. It will
be found in the shelter return air duct. See maintenance
instructions for shelter, and clean this filter.
Duct, Fresh Air
a. Check that inlet is not blocked and no source of fumes or excessive heat are
within 10 feet (3.1 meters) of the air inlet.
b. Inspect for cracks, dents, and punctures that would block airflow or allow
unfiltered air to enter air conditioner.
c. Wipe dust and dirt from inside surfaces with a clean cloth.
d. Reinstall the filter.
Cord, Elastic (Filter
a. Inspect for cuts, breaks, and excessive wear.
b. Check that it is in place and properly tied.
a. Check that hook is in good condition.
b. Check that hook is securely in place to retain filter.
|Integrated Publishing, Inc.|