(4) Starting with an end, carefully attach the insulation to the metal. Press into firm contact all over.
Replacement of name and information plates, riveted fasteners and lifting rings.
(1) Use a drill bit slightly smaller than the diameter of the rivet being removed.
(2) Drill the rivets out and remove the old part.
(3) Aline holes in replacement part and cover and install new rivets.
g. Minor dents and bent edges can be straightened using common sheet metal repair procedures. Panels that are
badly dented, bent, or punctured should be replaced.
h. Should touch up or refinishing be necessary, see paragraph 4-12.
4-17. RADIO FREQUENCY FILTER (FLI)
Preliminary Procedure: Remove air conditioner from shelter. (See paragraph 3-6.)
Figure 4-9. Radio Frequency Filter (FLI)
|Integrated Publishing, Inc.|