b. Removal- Model DHF
(1) Using screwdriver, tag and remove leads from thermostatic switch.
Figure 4-26. Thermostatic Switches (S2 and S3) - Model DHF
(2) Using stubby screwdriver, remove the three screws that hold the thermostatic switch bracket.
(3) Remove the switches and bracket from the unit.
(4) Using screwdriver and wrench, remove two each screws and lock nuts from each of the thermostatic
(5) Remove the switches from the bracket.
4-68.2 Change 2
|Integrated Publishing, Inc.|