(6) Using wrench, secure the coil with a nut.
(7) Connect leads to disconnect splices.
Follow-on Procedures: 1. Install top condenser cover. (See paragraph 3-25.)
2. Connect power.
4-70. SOLENOID VALVES (L1 AND L2)
For testing and coil replacement, see paragraph 4-69.
1. Disconnect power.
2. Remove top condenser cover. (See paragraph 3-25.)
3. Remove left end condenser cover. (See paragraph 3-27.)
If only the coil is bad, it can be replaced without breaking into the refrigerant
system. See paragraph 4-69.
|Integrated Publishing, Inc.|