Follow-on Procedures: 1. Install left end condenser cover. (See paragraph 3-27.)
2. Install top condenser cover. (See paragraph 3-25.)
3. Install the air conditioner on shelter. (See paragraph 3-6.)
4. Connect power.
4-86. TUBING AND FITTINGS (CONDENSER ASSEMBLY)
The condenser assembly contains a number of pieces of copper tubing in a variety of material grades, sizes, lengths, and
shapes and a number of elbows, tees, and adapters. Observe the following when replacing any piece of tubing or fitting
in the system:
1. Remove air conditioner from shelter. (See paragraph 3-6.)
2. Remove covers and parts as necessary to have access to repair area.
Figure 4-88. Refrigeration Piping, Condenser Section
|Integrated Publishing, Inc.|