(3) Refer to figure 4-10 and re-
move control module and junction box.
(1) Refer to figure 4-10 and in-
stall control module and junction box.
(2) Refer to figure 4-4 and in-
stall top front cover.
Control Module Components.
The control module com-
ponents consist of the compressor cir-
cuit breaker, control circuit breaker,
mode selector switch (rotary), tempera-
ture control switch, and the evaporator
fan speed relay switch.
have the same inspection and test re-
The compressor circuit
breaker is a safety device which pro-
vides overcurrent protection for the
The control circuit break-
er provides protection for the DC con-
Inspection and Test.
moving any of the control module compo-
nents-check for loose connections,
pitted contacts, and cracked or broken
Refer to wiring diagram (fig-
ure 1-5) and check for continuity with
If no continuity exists
with the circuit breaker in the ON posi-
tion, or if a casing is broken or
cracked, replace the circuit breaker.
BEFORE ATTEMPTING TO FULLY REMOVE CONTROL MODULE OR JUNCTION BOX, DISCONNECT
THERMOSTAT SENSING BULB FROM HOUSING AND CAREFULLY THREAD BULB THROUGH OPENING
DO NOT TURN CONTROL MODULE MOUNTING BOLT UNLESS UNIT HAS BEEN DISCONNECTED
FROM POWER SOURCE.
INSTALL JUNCTION BOX IN UNIT.
INSTALL CONTROL MODULE IN JUNCTION BOX.
OBSERVING CAUTION ABOVE ADD ATTACHING HARDWARE.
Junction box and control module, removal and installation