a. Remove two (2) screws securing compressor cover to
3. Cover Compressor
b. Remove cover from compressor to expose start capacitor
and start relay.
Death or serious injury may occur if capacitor is not discharged prior to
Remove two (2) hex nuts to loosen capacitor from bracket.
4. Start Capacitor
Remove cap from start capacitor.
Discharge start capacitor.
Tag and disconnect electrical leads from start capacitor.
LEFT SIDE OF HOUSING
a. Test start capacitor with a suitable capacitor tester for
5. Start Capacitor
b. The start capacitor is rated at 189 to 227 microfarads,
220 volts AC.
c. Replace start capacitor if testing indicates that it is defective.
a. Connect electrical leads to start capacitor and remove tags.
6. Start Capacitor
b. Cover electrical leads with cap.
c. Install start capacitor in bracket using two hex nuts.
7. Start Capacitor Cover a. Align two holes on compressor cover with holes on compressor.
b . Secure cover with two screws.
a. Align holes in left side panel with holes in housing.
8. Left Side Panel
b. Secure left side panel with seventeen (17) screws.