PRESSURE SWITCH (CONT.)
Connect. electrical connector (P-9)(12) to pressure
Align pressure switch (11) with holes in frame.
Secure pressure switch with three screws (10).
Assure sampling tubing is reinstalled in proper location to prevent
Connect sampling tubing to low pressure (13)
and high (14) pressure flare nuts and tighten.
Leak check, evacuate and charge system in
accordance with paragraphs 5-16 thru 5-18.