SERVICE VALVE (CONT.)
All refrigerant gas must be discharged from the system before proceeding
with the removal of the service valves.
Always perform inspection/test and adjustment before discharging system
to remove refrigeration component.
Discharge the system in accordance with paragraph
Remove 1/4 inch flare nuts (4) from service valves.
Remove two screws (6), two lock nuts (7)
and two flat washers (8) securing service
valve mounting bracket (9) to frame.
Remove service valve and service valve mounting
Remove two screws (10) and two lock washers
(11) securing service valves to service valve
Remove service valve from service valve mounting