THERMAL EXPANSION VALVE (CONT.)
Thermal Expansion Valve
Position bulb in same
Secure sensing bulb to suction line with two band
Wrap the sensing bulb (6) with insulating tape
(Item 6, table D-1) being careful to avoid kinking
position as it was removed.
Carefully install the sensing bulb to its position
on the suction line.
Clamp into position on the
Cover suction line, sensing bulb and
clamps with insulating material.
Carefully form the capillary tube along adjacent
Leak check, evacuate and charge system in
accordance with paragraphs 5-16 thru 5-18.