QUENCH VALVE (CONT.)
All refrigerant gas must be discharged from the system before proceeding
with the removal of the quench valve.
Always perform inspection/test and adjustment before discharging system
to remove refrigeration component.
Discharge the system in accordance with paragraph
Note position of bulb on removal and be sure to replace in same position.
Remove insulation (14) and band clamps from sensing
Carefully detach bulb and capillary
Remove two cap screws (15) securing the power
assembly (16) to the flanged base (17).
Remove the power assembly, capillary tube (19)
and sensing bulb (18).