5-32 RECEIVER (CONT.)
All refrigerant gas must be discharged from the system before proceeding
with the removal of the receiver.
Always perform inspection/test and adjustment before discharging system
to remove refrigeration component.
Discharge the system in accordance with paragraph
Remove flare nut (8) on drier (4).
Remove four screws (6) securing receiver mounting
bracket (7) to frame.
Remove drier and receiver assembly.
Remove one nut (9) securing receiver to
receiver mounting bracket.
Remove mounting band (10) from receiver (11) and
Debraze receiver in accordance with paragraph