a. Inspect for damage.
Repair or replace if damaged.
a. Disconnect plug (P1), from the electrical junction
box on the compressor.
Remove wing nut (11) securing compressor
junction box cover (12) to compressor.
Remove compressor junction box cover.
Schematic is not correct red, white and black wires are yellow wires
striped with red, white and black respectively.
Using a multimeter check for continuity.
Test compressor receptacle pins A-B, A-C,
B-C, and D-E. Continuity should be
Test points A, B and C to
compressor casing or common ground. No
continuity should be indicated.
compressor that does not meet continuity