CONDENSER COIL (CONT.)
R E M A R KS
All refrigerant gas must be discharged from the system before proceeding
with the removal of the condenser coil.
Always perfom inspection/test and adjustment before discharging system
to remove refrigeration component.
system in accordance with
Debraze condenser coil (12) in accordance
with paragraph 5-15.
Remove two countersunk screws (13) and two
lock nuts (14) securing outside upper
condenser coil bracket (15) to frame.
Remove two screws (16) and two flat washers
(17) securing outside upper condenser coil
bracket to condenser coil.
Remove outside upper condenser coil bracket.