EVAPORATOR COIL (CONT.)
All refrigerant gas must be discharged from the system before proceeding
with the removal of the evaporator coil.
Always perform inspection/test and adjustment before discharging system
to remove refrigeration component.
Discharge system in accordance with
Debraze evaporator coil (16) in accordance with
Remove two screws (17), two flat washers (18)
and two lock nuts (19) securing upper
evaporator coil bracket (20) to frame.
Remove two screws (21) and two flat
washers (22) securing upper evaporator
coil bracket to evaporator coil.
Remove upper evaporator coil braoket.