G E N E R A L .
To insure that the air conditioner is ready for
be inspected systematically so that the defects
before the result is serious damage or failure.
operation of the unit shall be noted for future
operation at all times, it must
may be discovered and oorrected
Defects discovered during
corrections to be made as soon
as an operation has ceased.
Stop operation which would damage the equipment
if operation were to continue.
All deficiencies and shortcomings shall be
recorded together with the corrective action taken on DA Fom 2404 "Equipment
Inspection and Maintenance Worksheet", at the earliest opportunity. If your
equipment fails to operate, troubleshoot with proper equipment.
deficiencies using proper forms, (See DA PAM 738-750).
4-10. PREVENTIVE MAINTENANCE CHECKS AND SERVICES (PMCS).
Dry cleaning solvent, P-D-680, or P-S-661, used to clean
parts is potentially dangerous to personnel and property.
Avoid repeated and prolonged skin contact. Do not use
near open flame or excessive heat.
Flash point of solvent
is 100 degrees F (38 degrees C).
Do not use compressed air for cleaning purposes except where
reduced to less than 30 psi (2.11 km/ cm 2) and then only with
effective chip guarding and personal protective equipment.
Change 1 4 - 7