TEST OR INSPECTION
S t e p 3 .
Check for correct operation of condenser fan assembly.
Replace or repair damaged condenser fan
assembly in accordance with paragraph
fresh air dampers.
Remove eight screws and eight rubber washers
securing lifting ring covers to top panel and
Remove lifting ring covers.
Remove twenty-three screws and eight screws
securing top panel to frame.
Remove top panel.
Inspect for freedom of movement, lubricate if
required (Item 17, table D-1).
Tighten loose mountings.
Replace or repair fresh air dampers, in
accordance with paragraph 4-20.