4-26. RUN CAPACITOR (CONT)
LEFT SIDE OF HOUSING
a. Test run capacitor with a suitable capacitor tester for
3. Run Capacitor
b. The run capacitor is rated at 35 microfarads, 370 volts.
c. Replace run capacitor if testing indicates that it is defective.
4. Run Capacitor
a. Install run capacitor in capacitor bracket.
b. Tighten capacitor bracket screw.
c. Connect electrical leads to run capacitor and remove tags.
d. Cover electrical leads with cap.
5. Left Side Panel
a. Align holes in left side panel with holes in housing.
b. Secure left side panel with seventeen (17) screws.