Table 4-1. Troubleshooting (continued)
TEST OR INSPECTION
Inspect and test pressure equalizer solenoid valve (paragraph 3-13c).
Repair or replace damaged or defective pressure equalizer solenoid valve
Check for insufficient refrigerant in system (bubbles in sight glass).
Add refrigerant (paragraph 4-11).
If adding refrigerant to the system does not clear up bubbles in sight glass, there may be air
in the system.
evacuate system (figure 4-4), and recharge the system with refrigerant
Check for inoperative fans.
Perform corrective actions listed for malfunction 10 of this troubleshooting table.
Check air conditioner operating pressures for excessive refrigerant in system (table 4-3).
Release excess refrigerant from system until the proper charge is attained
Inspect expansion valve and check superheat (paragraph 4-15).
Repair or replace damaged or defective expansion valve. Adjust expansion valve if
superheat is not correct (paragraph 4-15).
Inspect quench valve and check superheat (paragraph 4-16).
Repair or replace damaged or defective quench valve.
Adjust quench valve if
superheat is not correct (paragraph 4-16).
Inspect and test liquid line solenoid valve (paragraph 3-13d).
Repair or replace damaged or defective liquid line solenoid valve (paragraph 4-17).
|Integrated Publishing, Inc.|