THERMAL EXPANSION VALVE (CONT.)
All refrigerant gas must be discharged from the system before proceeding
with the removal of the thermal expansion valve.
Always perform inspection/test and adjustment before discharging system
to remove refrigeration component.
Discharge the system in accordance with paragraph
Remove insulation (4) and band clamps (5) from
sensing bulb (6). Carefully detach bulb and
Remove two capscrews (7) securing power assembly
(8) to the flanged base (9).
Remove the power assembly, capillary tube and sen-
equalizer line (10) on thermal expansion