Figure 4-98. Time Delay Relay (K6)
(7) Turn mode selector switch to COOL and temperature control to maximum COOLER.
(8) Multimeter should show 25 to 31 Vdc for 15 to 60 seconds and then zero Vdc across terminals 1 and 2.
(9) Turn mode selector switch to OFF.
(10) Disconnect power.
(1) Check for loose terminal connections. Repair or replace all loose connections.
(2) Check for cracks, evidence of overheating, and other visible damage. Replace if damaged.
|Integrated Publishing, Inc.|