b. Make sure the unit has capacity to cool the space in which it is
c. Connect the unit to 115 volt, single phase, 60-cycle only.
d. Make sure the unit is sealed so that no air will escape around
e. The unit must be installed so that there is access to either
the bottom panel (filter opening) or the top panel for access to the
f. Connect a drain hose to the bottom pan even though the lower
filter access panel is not used. Make sure the filter has two rubber
pads on the bottom and is not resting on the drain hole, or the bottom
pated during the installation in the particular installation.
h. There are two threaded holes under the unit 1 inch from each
side to which mounting bolts should be installed through the above
brackets (figure 2).
MOVEMENT TO NEW WORKSITE
Dismantling for Movement
a. Disconnect the power supply cord assembly.
Remove all mounting bolts under the unit (para 9).
c. Remove all sealing angles from around unit.
Carefully slide the unit from the wall.
e. Use wood blocking and steel strapping to secure the unit to
carrier for long distance moving.
11. Reinstallation After Movement
Reinstall after movement as specified in paragraph 9.
CONTROLS AND INSTRUMENTS
This section describes, locates, illustrates, and furnishes the op-
erator, crew or maintenance personnel information pertaining to the
various controls and instruments for proper operation of the air condi-