Remove low pressure switch. (See paragraph 4-81.)
Remove compressor. (See paragraph 4-88.)
11. Remove relief valve and related piping. (See paragraph 4-82.)
(1) While purging the system with nitrogen, debraze the remaining tubing from the coil and area of the coil. (See
(2) Using screwdriver, remove the ten screws that attach the coil to the housing.
When handling coils, wear gloves to avoid cuts and reduce fin damage on the coil.
Figure 4-87. Condenser Coil
|Integrated Publishing, Inc.|